title: [On bacterial aftergrowth in drinking and industrial water. II. Apparative and processing influence upon the growth and the possibility of disinfection of ion exchange resin filter systems (author's transl)].
abstract: The comparative examination of numerous ion exchange resin filter systems for discontinuous water softening on the market revealed that apparative and processing characteristics are of great influence upon the aftergrowth of bacteria in the water of ion exchange resin systems. Within the examination it was taken into consideration that on the end-delivery-tube of the water pipe with regard to the colony count the conditions were more unfavourable during the long standstill over a weekend (table 1) than during the week (table2). The less favourable conditions have therefore been examined separately. The work has been divided in six test series. In the first one 5 ion exchange resin systems the types A-E are simultaneously tested with regard to the colony count in the water at the inflow to the apparatus and after the passage of it; regeneration twice a week with sodium chloride. The data ascertained in the course of several weeks (without first data on mondays) and the separated mondays data are examined according to logarithmic transformation with the assistance of variance analysis and the Newman Keuls-test for differences. The results show (tab. 4 and 5) that apparative parameters and such relevant to the technical process (tab. 3) have an influence upon the bacterial after growth of the water. The most favourable ion exchange resin filter is type E because it shows more favourable values than all other systems and the tapwater. In the second test serie the systems A-E have been regenerated with 1% Chloramin T containing sodium chloride. The results show again the type E as the statistically significant most favourable system in comparison with the others and the tapwater. In the third test serie it has been examined whether the long period of standstill of the brine in the resin bed which has probably been responsible for the good results of the type E would lead to values just as favourable if transferred to another type of apparatus. ...
mesh_terms: D001419:Bacteria / Q000187:drug effects / Q000254:growth & development*; D002452:Cell Count; D002700:Chloramines / Q000494:pharmacology; D004203:Disinfection; D005069:Evaluation Studies as Topic; D005374:Filtration / Q000295:instrumentation*; D007475:Ion Exchange Resins; D012965:Sodium Chloride / Q000494:pharmacology; D013242:Sterilization; D014871:Water Microbiology; D014876:Water Pollution; D014881:Water Supply
chemical_list: D002700:Chloramines; D007475:Ion Exchange Resins; D012965:Sodium Chloride
vernacular_title: Zur Frage der Nachverkeimung von Trink- und Brauchwasser. II. Apparative und verfahrenstechnische Einflüsse auf die Verkeimung und die Möglichkeit zur Desinfektion von Ionenaustauscheranlagen