[Microbial contamination in a water-treatment system].
Microorganisms destructors of organic compounds contained in the Kremenchug reservoir and water treatment system of heat power station have been distinguished and identified. This system does not completely remove microflora at all stages of technological process that results in infestation of ion-exchange resins of the 1st stage filters for water desalting with microorganisms. The reasons have been established of the 1st stage desalting filters infestation by the reservoir water microflora. It is necessary to form a complex approach to solution of the problem of preventing the accident situations: microbe infestation of ion-exchange resins of water-desalting filters in the system of chemical water treatment of heat power stations.
Roĭ
A A
AA
Koval'
E Z
EZ
Iakushin
V M
VM
D001419:Bacteria / Q000302:isolation & purification; D004866:Equipment Contamination; D005374:Filtration / Q000295:instrumentation; D007475:Ion Exchange Resins; D011210:Power Plants / Q000295:instrumentation; D014455:Ukraine; D014871:Water Microbiology; D018508:Water Purification / Q000295:instrumentation; D014881:Water Supply
D007475:Ion Exchange Resins
Mikrobnoe zagriaznenie v sisteme vodopodgotovki.