Hospital generator sizing, testing, and exercising.
With the NFPA 99 and JCAHO requirements for minimum loads on generators during testing, hospital engineers are finding that oversized standby generators can mean operational problems. This document explains the oversized generator problem, including the code changes that gave birth to the problem. Some practical suggestions for sizing generators are then provided.
Nash
H O
HO
Smith Seckman Reid, Inc., Nashville, TN.
D002028:Building Codes / Q000592:standards*; D011211:Electric Power Supplies / Q000592:standards*; D004867:Equipment Design / Q000592:standards; D005390:Fires / Q000517:prevention & control; D007591:Joint Commission on Accreditation of Healthcare Organizations; D008284:Maintenance and Engineering, Hospital / Q000592:standards*; D017751:Safety Management; D012952:Societies; D014481:United States