Thermal loading as a causal factor in exceeding the 0.1 PPM laboratory fume hood control level.
Tracer gas testing per ANSI/ASHRAE 110-1995 Method of Testing Performance of Laboratory Fume Hoods was used to investigate the role of thermal loading in exceeding laboratory fume hood control levels. Three types of typical laboratory burners (blast, Meeker, and economy) were used to provide a thermal challenge. Heat outputs of between 0 and 61,610 Btu/hr were based on fuel heat capacity (for liquid propane gas) and fuel gas flow rates. Breathing zone concentrations were measured with a MIRAN 1B2 infrared gas analyzer. Also, for each test, the difference between the room and duct temperatures (delta temperature) was measured. Results indicated a linear relationship between heat loads and tracer gas breathing zone concentrations for both Btu/hr and delta temperature. Control levels of 0.1 ppm were exceeded at less than 12,000 Btu/hr. Also, control levels were exceeded at a lower heat load when the tracer gas generation rate was increased. These results indicate that thermal loads in laboratory fume hoods increase the risk of exceeding laboratory fume hood control levels. Some compensatory measures relative to hood configuration and flow rates are recommended for laboratory operations involving heat sources.
Chessin
Saul J
SJ
Idaho National Engineering and Environmental Laboratory, Idaho Falls, USA.
Johnston
James D
JD
D016902:Air Pollution, Indoor / Q000517:prevention & control*; D020378:Confined Spaces; D004784:Environmental Monitoring / Q000295:instrumentation / Q000379:methods*; D006801:Humans; D007753:Laboratories; D008452:Maximum Allowable Concentration; D016273:Occupational Exposure / Q000517:prevention & control*; D016272:Occupational Health; D014481:United States; D014691:Ventilation / Q000295:instrumentation* / Q000592:standards