Detention storage volume for combined sewer overflow into a river.
This article discusses the storage volume needed in a combined sewer system tank in order to preserve the water quality. There are a lot of design criteria which do not take into account the conditions of the receiving water, and as a result are inappropriate. A model was used to simulate the performance of a theoretical combined sewer system where a tank was located downstream. Results were obtained from the overflows produced by the rain recorded in Santander (Spain) for 11 years, with several combinations of storage volume and treatment capacity in the wastewater treatment plant. Quality criteria were also proposed for faecal coliforms, BOD, and total nitrogen to evaluate the effects from the overflows in the river water quality. Equations have been obtained which relate the number of overflows, the storage volume and the treatment plant capacity. The bacteriological pollution, quantified by means of faecal coliforms, was the analytical parameter which produced the most adverse effects in the river, so that more storage volume is needed (45 to 180 m3 ha(-1) net) than with other simulated pollutants (5 to 50 m3 ha(-1) net for BOD, and less than 4 m3 ha(-1) net for the total nitrogen). The increase in the treatment plant's capacity, from two to three times the flow in dry weather, reduces the impact on the river water in a more effective way, allowing a reduction of up to 65% in the number of overflows rather than increasing the storage volume.
Departamento de Ciencias y Técnicas del Agua y del Medio Ambiente, EU.I.T. Minera-Ingeniería Ambiental, Universidad de Cantabria, Torrelavega, Spain.
J
J
Temprano
I
I
Tejero
D004755:Enterobacteriaceae / Q000302:isolation & purification; D009584:Nitrogen / Q000032:analysis; D010100:Oxygen / Q000032:analysis; D011891:Rain; D012722:Sewage; D014871:Water Microbiology; D014872:Water Movements; D014876:Water Pollution / Q000517:prevention & control*
D012722:Sewage; D009584:Nitrogen; D010100:Oxygen