title: Comparison of discharge silver concentrations from electrolytic plating and metallic replacement silver recovery units.
abstract: Silver-based photographic X-ray film is made of solid crystals of silver chloride or silver bromide suspended in a gelatin and then coated on a film. During the X-ray developing process, the image is processed and the nonimage areas containing solid silver chloride or silver bromide crystals are removed in a solution called the fixer. There may be local environmental regulations that regulate the amount of silver discharged from a facility. To meet these regulations, many facilities have added silver recovery units to their processes. Two different types of recovery processes are in use in a large hospital and three clinics under study. All of the units were claimed by their respective manufacturers to be able to recover silver down to concentrations of 5 mg/L. This concentration would ensure that the building that houses each unit would meet the local county limit of 0.5 mg/L silver for total building silver discharge. The hypothesis for this research is that one system, newer and more expensive, consisting of so-called electrolytic plating units (EPUs) (which are followed by so-called metallic replacement units [MRUs] as a backup), will have better silver recovery than MRUs alone. A total of six units were sampled, three EPUs (in combination with MRUs) and three MRUs. The units were sampled once or twice a day for 10 days for a total of 17 samples from each. The samples then were analyzed by inductively coupled plasma spectroscopy, and an analysis of variance was performed on the results. The range for the electrolytic plating unit/metallic replacement unit combinations was 0.20-99.9 mg/L (mean of 35.15 mg/L; median of 33.8 mg/L). The range for the MRUs alone was 7.2-1112 mg/L (mean of 565.5 mg/L; median of 720 mg/L). Many individual results exceeded 5 mg/L, such that extensive dilution would be required to ensure the building effluent did not exceed 0.5 mg/L. It is suggested that the metallic replacement units be changed to EPUs (with metallic replacement backup units) because they had better silver recovery. Also, the EPU combinations need to be sampled regularly to ensure that their silver concentrations are at acceptable levels.
authors.affiliation: Department of Environmental Health Sciences, School of Public Health, University of Alabama, Birmingham, Alabama, USA. mharper@cdc.gov
authors.forename: Martin
authors.initials: M
authors.lastname: Harper
authors.forename: Julie M
authors.initials: JM
authors.lastname: Siegel
mesh_terms: D003247:Conservation of Natural Resources / Q000191:economics; D003362:Cost-Benefit Analysis; D004595:Electroplating; D004787:Environmental Pollution / Q000517:prevention & control; D007220:Industrial Waste; D010781:Photography; D012834:Silver / Q000032:analysis*
chemical_list: D007220:Industrial Waste; D012834:Silver