Exposure of a liquefied gas container to an external fire.
In liquefied gas, bulk-storage facilities and plants, the separation distances between storage tanks and between a tank and a line of adjoining property that can be built are governed by local regulations and/or codes (e.g. National Fire Protection Association (NFPA) 58, 2004). Separation distance requirements have been in the NFPA 58 Code for over 60 years; however, no scientific foundations (either theoretical or experimental) are available for the specified distances. Even though the liquefied petroleum gas (LPG) industry has operated safely over the years, there is a question as to whether the code-specified distances provide sufficient safety to LPG-storage tanks, when they are exposed to large external fires. A radiation heat-transfer-based model is presented in this paper. The temporal variation of the vapor-wetted tank-wall temperature is calculated when exposed to thermal radiation from an external, non-impinging, large, 30.5 m (100 ft) diameter, highly radiative, hydrocarbon fuel (pool) fire located at a specified distance. Structural steel wall of a pressurized, liquefied gas container (such as the ASME LP-Gas tank) begins to lose its strength, when the wall temperature approaches a critical temperature, 810 K (1000 degrees F). LP-Gas tank walls reaching close to this temperature will be a cause for major concern because of increased potential for tank failure, which could result in catastrophic consequences. Results from the model for exposure of different size ASME (LP-Gas) containers to a hydrocarbon pool fire of 30.5 m (100 ft) in diameter, located with its base edge at the separation distances specified by NFPA 58 [NFPA 58, Liquefied Petroleum Gas Code, Table 6.3.1, 2004 ed., National Fire Protection Association, Quincy, MA, 2004] indicate that the vapor-wetted wall temperature of the containers never reach the critical temperature under common wind conditions (0, 5 and 10 m/s), with the flame tilting towards the tank. This indicates that the separation distances specified in the code are adequate for non-impingement type of fires. The model can be used to test the efficacy of other similar codes and regulations for other materials.
Raj
Phani K
PK
Technology and Management Systems, Inc., Burlington, MA 01803, USA. tmsinc1981@verizon.net
D004781:Environmental Exposure / Q000032:analysis / Q000517:prevention & control / Q000592:standards; D005107:Explosions / Q000517:prevention & control*; D005390:Fires; D005579:Fossil Fuels; D006358:Hot Temperature; D007221:Industry / Q000592:standards; D008962:Models, Theoretical; D019064:Product Packaging / Q000592:standards*; D013499:Surface Properties
D005579:Fossil Fuels