title: Lime enhanced chromium removal in advanced integrated wastewater pond system.
abstract: The removal of trivalent chromium from a combined tannery effluent in horizontal settling tanks and subsequent Advanced Integrated Wastewater Pond System (AIWPS) reactors was investigated. The raw combined effluent from Modjo tannery had pH in the range of 11.2-12. At this pH, a trivalent chromium removal of 46-72% was obtained in the horizontal settling tanks after a one-day detention time. Trivalent chromium precipitated as chromium hydroxide, Cr(OH)3. 58-95% Cr(III) was removed in the advanced facultative pond (AFP) where the water column pH of 7.2-8.4 was close to pH 8, which is the optimum precipitation pH for trivalent chromium. Chromium removals in the secondary facultative pond (SFP) and maturation pond (MP) were 30-50% and 6-16%, respectively. With Cr(III) concentration of 0.2-0.8 mg/l in the final treated effluent, the AIWPS preceded by horizontal settling tanks produced effluent that could easily meet most of the current Cr(III) discharge limits to receive water bodies.
authors.affiliation: Institute of Environmental Engineering and Biotechnology, Tampere University of Technology, P.O. Box 541, 33101 Tampere, Finland. issayas.tadesse@sbcglobal.net
authors.forename: I
authors.initials: I
authors.lastname: Tadesse
authors.forename: S A
authors.initials: SA
authors.lastname: Isoaho
authors.forename: F B
authors.initials: FB
authors.lastname: Green
authors.forename: J A
authors.initials: JA
authors.lastname: Puhakka
mesh_terms: D017610:Calcium Compounds / Q000737:chemistry*; D002857:Chromium / Q000737:chemistry*; D006863:Hydrogen-Ion Concentration; D010087:Oxides / Q000737:chemistry*; D013053:Spectrophotometry; D013633:Tanning; D014865:Waste Disposal, Fluid / Q000379:methods*; D014874:Water Pollutants, Chemical / Q000032:analysis*; D018508:Water Purification / Q000379:methods*
chemical_list: D017610:Calcium Compounds; D010087:Oxides; D014874:Water Pollutants, Chemical; D002857:Chromium; C016538:lime