Upgrading of the STP Uithoorn: treatment of nutrient rich wastewater from horticulture.
The STP Uithoorn will be upgraded to accommodate the treatment of wastewater from a growing population and to meet more stringent nutrient discharge limits in 2006. In 2003 a system choice and preliminary design was made for the upgrading. A special feature is the nutrient rich wastewater flow from the rapidly developing horticulture in the area. Since the future loads from horticulture are highly uncertain, flexibility of the STP after upgrading is an important issue. A three stage system was selected: improved physical-chemical primary treatment, secondary treatment by activated sludge, and tertiary treatment by denitrifying filters. In this way an important part of the existing infrastructure can be reused, and flexibility is assured by constructing the tertiary treatment in modules and by providing a wide range of operational control possibilities. In this paper the process of system choice and selection of type of tertiary treatment are described, as well as the optimisation of the existing treatment. In order to determine the feasibility of allowing a high loading rate on the existing secondary clarifiers, a two-dimensional hydraulic model of the clarification process was used.
Piekema
P
P
AGV (Waterboard Amstel Gooi and Vecht), P.O. Box 94370, 1090 GJ Amsterdam, The Netherlands. peter.piekema@dwr.nl
Neef
R
R
D000383:Agriculture; D019149:Bioreactors; D009566:Nitrates / Q000032:analysis / Q000302:isolation & purification; D010710:Phosphates / Q000032:analysis; D012722:Sewage / Q000737:chemistry; D018508:Water Purification / Q000379:methods*
D009566:Nitrates; D010710:Phosphates; D012722:Sewage