Is ultraviolet radiation on haemodialysis RO water beneficial?
The quality of dialysis fluids has become increasingly important in the treatment of HD patients. Purified water represents over 95% of its volume. Bacterial and endotoxin content of Reverse Osmosis (RO) water is usually kept under control by bacterial filters, inserted in the distribution departure loop, and by monthly disinfection of the distribution circuit; the simpler the circuit, the better. This paper reports 12 years experience during which Ultraviolet Irradiation (UV) has replaced bacterial filters. To keep the bacterial growth under control in a complex RO water circuit (including a tank and multiple loops) a simple UV lamp was inserted in the departure line. It proved sufficient to keep bacterial count within AAMI norms. Failure of the UV lamp was associated with a rise of up to 500 cfu/ml in the last (fourth week) before routine disinfection. Normal levels were again obtained after replacement of the UV lamp. Six years later, a second UV lamp was added on the return loop. Bacterial counts and endotoxin levels in RO water promptly fell to <1 cfu/ml and <0.125 EU, till today. It is concluded that UV lamps should be favoured over bacterial filters in systems that are not disinfected daily, such as the RO water circuit. The principle of UV irradiation is explained and its advantage over bacterial filters is discussed. Future possible applications of UV are presented.
Stragier
A
A
Université Catholique de Louvain, Renal Unit, Brussels, Belgium. Andre.Stragier@telenet.be
D015169:Colony Count, Microbial; D004203:Disinfection; D004731:Endotoxins / Q000032:analysis; D015312:Hemodialysis Solutions; D006801:Humans; D009995:Osmosis; D006435:Renal Dialysis; D014466:Ultraviolet Rays; D014867:Water; D014871:Water Microbiology
D004731:Endotoxins; D015312:Hemodialysis Solutions; D014867:Water