title: The 'fine line' of heat rejection.
abstract: Selection of heat rejection equipment has traditionally entailed a choice between the higher energy consumption of an air-cooled solution, and the high water consumption of a water-cooled solution. This paper examines advancement in heat rejection technology and the way it can be applied to air conditioning and refrigeration plant in healthcare and other facilities. It also examines field difficulties encountered in pipework design as the knowledge and experience levels of engineers designing systems with remote condensers diminish. With plant larger than 1,000 kW, the only option previously has been water-cooled solutions using an array of cooling towers, or perhaps an evaporative condenser, since air-cooled plant involved massive volumes of chemical refrigerant, which posed a problem ecologically. An additional hurdle was problems associated with limitations on pipe lengths for refrigeration plant. The advent of adiabatically pre-cooled closed circuit coolers and air-cooled condensers has introduced an alternative to cooling towers that offers the potential for "water-cooled performance" from an air-cooled solution with no serious threat of Legionella contamination. However, each application needs to be considered on a case-by-case basis. The paper examines, in detail, the impact of adiabatic pre-cooling, with recent examples of its application in sub-tropical Brisbane providing evidence of the potential performance achievable.
authors.affiliation: Norman Disney & Young, Brisbane.
authors.forename: Phillip
authors.initials: P
authors.lastname: Carruthers
mesh_terms: D000389:Air Conditioning / Q000295:instrumentation* / Q000379:methods*; D006268:Health Facilities; D013672:Technology; D006113:United Kingdom