Passive vapor monitoring of underground storage tanks for leak detection.
Passive vapor monitoring of underground storage tanks (USTs) containing volatile hydrocarbons at locations external to the tank (an external system) is touted as a fast and effective method of leak detection. However, major gaps remain in our knowledge of the physical processes that relate a measured vapor concentration to the leak rate, thus making network design according to a quantitative design criterion nearly impossible, and differentiation between surface spills and a leaking UST requires certain levels of sophistication in the leak detection system and in the analysis that are not usually available. Heavier-than-air vapors from the constituents of stored hydrocarbons could result in a density-driven convective propagation component that complicates the design of leak detection systems, and finally, detection times are highly sensitive to concentration detection threshold levels set by the system. The use of inadequate systems and analyses can lead to either wasted efforts or excessive subsurface contamination. This paper discusses the physical processes involved, explores the above aspects of external passive vapor leak detection design, and suggests some alternatives as they pertain to gasoline service stations.
Environmental Research Center, University of Nevada, Las Vegas, 89154, Las Vegas, Nevada, USA.
D
D
Weber
F
F
Schwille