Note: control of liquid helium supply to cryopanels of Kolkata superconducting cyclotron.
The Kolkata superconducting cyclotron utilises liquid helium to cool the main magnet niobium-titanium (NbTi) coil and the cryopanels. Three liquid helium cooled cryopanels, placed inside the dees of the radio-frequency system, maintain the high vacuum in the acceleration region of the superconducting cyclotron. The small cryostat placed inside the cryogenic distribution manifold located at the basement of the superconducting cyclotron building supplies liquid helium in parallel branches to three cold heads, used for cooling their associated cryopanels. The level in the cryostat has to be maintained at an optimum value to ensure uninterrupted flow of liquid helium to these three cold heads. This paper describes the transfer function of the overall system, its tuning parameters, and discusses the actual control of cryostat level by using these parameters.
Variable Energy Cyclotron Centre, 1/AF Bidhan Nagar, Kolkata 700 064, India.
T K
TK
Bhattacharyya
Variable Energy Cyclotron Centre, 1/AF Bidhan Nagar, Kolkata 700 064, India.
G
G
Pal