title: Energy Use Consequences of Ventilating a Net-Zero Energy House.
abstract: A Net-Zero Energy Residential Test Facility (NZERTF) has been constructed at the National Institute of Standards and Technology (NIST) in Gaithersburg, Maryland to demonstrate that a home similar in size, aesthetics, and amenities to those in the surrounding communities can achieve net-zero energy use over the course of a year while meeting the average electricity and water use needs of a family of four in the United States. The facility incorporates renewable energy and energy efficient technologies, including an air-to-air heat pump system, a solar photovoltaic system, a solar thermal domestic hot water system, and a heat recovery ventilation system sized to meet American Society of Heating, Refrigeration, and Air-Conditioning Engineers (ASHRAE) Standard 62.2-2010 ventilation requirements. The largest energy end use within the home was space conditioning, which included heat loss through the building envelope, ventilation air supplied by the heat recovery ventilator (HRV), and internal loads. While HRVs are often described as being able to save energy when compared to ventilating without heat recovery, there have been no studies using a full year of measured data that determine the thermal load and energy impacts of HRV-based ventilation on the central heating and cooling system. Over the course of a year, continuous operation of the HRV at the NZERTF resulted in an annual savings of 7 % in heat pump energy use compared with the hypothetical case of ventilating without heat recovery. The heat pump electrical use varied from an increase of 5 % in the cooling months to 36 % savings in the heating months compared with ventilation without heat recovery. The increase in the cooling months occurred when the outdoor temperature was lower than the indoor temperature, during which the availability of an economizer mode would have been beneficial. Nevertheless, the fan energy required to operate the selected HRV at the NZERTF paid for itself in the heat pump energy saved compared with ventilation without heat recovery.
authors.affiliation: Indoor Air Quality and Ventilation Group, Energy and Environment Division, National Institute of Standards and Technology, 100 Bureau Drive, MS 8633, Gaithersburg, MD 20899, USA.
authors.forename: Lisa C
authors.initials: LC
authors.lastname: Ng
authors.affiliation: HVAC&R Equipment Performance Group, Energy and Environment Division, National Institute of Standards and Technology, 100 Bureau Drive, MS 8633, Gaithersburg, MD 20899, USA.
authors.forename: W Vance
authors.initials: WV
authors.lastname: Payne
keywords: air-to-air heat pump; heat recovery ventilator; net-zero energy buildings; ventilation energy use